100% Brand new and High quality!
Electronic tool equipment smart-family. The product as described in the picture.
Excellent quality, fast delivery, simple after-sales We make every effort to provide customers with satisfactory service
Control range: -50°C to 110°C
Control accuracy: 0.1°C
Measurement input: NTC10K waterproof sensor L=0.5M
High-temperature alarm: -49°C to 110°C
Input voltage: DC 12V
Output type: relay output up to 10A
Return difference setting: 0.1°C to 30°C
Delayed start: 0-10 minutes
Temperature correction: -10°C to +10°C
Size: 60*43*16mm (length*width*height)
How to restore factory settings:
Under normal power, press and hold the + and - key for about three seconds to restore factory settings.
1. PO temperature control mode:
This value must be set when the thermostat is used for the first time. If it is used for heating, it must be set to H. If it is used for cooling, it should be set to C.
2. P1 difference setting:
Press the SET button for a long time to enter the internal settings, select the P1 setting, and then press the SET button again to set the hysteresis value. (The hysteresis is the difference needed when the thermostat reaches the set temperature and stops working again.)
3. P2 temperature calibration:
This function is used for temperature calibration. If there is a deviation between the detected temperature and the actual temperature, this function can be used to correct. The corrected value = measured value + correction value. (If you do not control the compressor or do not need delay function, skip this item directly)
4. P4 high-temperature alarm:
Set the high-temperature alarm value. When the real-time temperature exceeds this value, the screen will flash warning alarm.